Requirements for Electric Service Connection
From page 61 of handbook……..
"Starting Limitations. Reduced starting current shall be required on all motors
exceeding 15 horsepower nameplate rating, unless otherwise agreed to by the
Utility. The customer shall furnish details of motor characteristics for all motors
larger than 15 horsepower at which time the Utility will determine the maximum
allowable starting current for a given installation. Across-the-line starting of the
customer's motors of 15 horsepower and less will normally be permitted. When
the locked rotor current of a motor exceeds the valve listed in Table V of the
motor will be started more frequently than one start per hour, the utility may
require the use of a suitable starting device to limit the starting current. Upon
failure to install the required starting device, the Utility shall disconnect the
service. Reconnection shall be at the customer's expense."
Property of Dave's Pump Service, Inc.
Intended for information purposes only.
Dave's Pump Service, Inc is not responsible for content